Panasonic WhisperWarm / Warm Lite Ceiling mount fan / heater / Light 110 CFM FV-11VHL2
Ventilating fan shall be low noise ceiling mount type rated for continuous run. Fan shall be certified by the Home Ventilating Institute (HVI). Fan shall include energy efficient compact fluorescent lighting and night-light. Heating element shall be included. Evaluated by Underwriters Laboratories and conform to both UL and cUL safety standards. Fan is not intended for installation over a tub/ shower enclosure.
KEY FEATURES:Four–pole totally enclosed condenser motor rated for continuous run.
Power rating shall be 120 volts and 60 Hz.
Motor equipped with thermal–cutoff fuse.
Permanently lubricated plug–in motor
Rust proof paint, galvanized steel body.
4" diameter duct adapter.
Built-in backdraft damper.
Attractive design using ABS material.
Attaches directly to housing with torsion springs.
Two 13 Watt self-ballasted GU24 base CFL lamps
One 4-Watt night–light included.
Tubular steel sheathed heating element. Nichrome wire with magnesium oxide for optimal heat transfer and electrical insulation at elevated temperatures.
90 CFM super quiet, energy efficient blower motor.
Quick 1-minute warm-up.
3-Year limited warranty on all parts. Compact Fluorescent Lamps (CFL): 1 Year. No warranty on night-light
SPECIFICATIONS:A ventilation fan, heater, light and night-light combination shall be ceiling mount, with no less than 110 CFM and no more than 0.7 sone as certified by HVI at .1 static pressure in inches water gauge (w.g.) with no less than 89 CFM and no more than 1.0 sone at .25 w.g. Power consumption shall be no greater than 30.6 Watts at .1 w.g. and 30.5 Watts at .25 w.g. With an efficiency of no less than 3.6 CFM/Watt at . w.g. and 2.9 CFM/Watt at .25 w.g.
The motor shall be totally enclosed, 4 pole condenser type engineered to run continuously.
Power rating shall be 120v/60Hz. Duct diameter shall be no less than 4".
Fan is not intended for installation over a tub/shower enclosure.
Fan shall be ASHRAE 62.2, LEED, EarthCraft, California Title-24, and WA Ventilation Code compliant.
Lamps utilize no less than two 13 Watt self-ballasted GU24 base ESTAR rated compact fluorescent lamps. Night-light shall be included.
Heating element shall be Nichrome wire in tubular steel sheath construction with magnesium oxide for optimal heat transfer.
Heating element power consumption shall be no less than 1400 watts. Heating feature shall include a 90 CFM blower fan with energy efficient condenser type motor with a quick 1-minute warm-up.